We are a topmost name in procuring industry, who are indulged in getting superior quality Liva ESE lightning Arrester. It is known to be the best and safest early streamer emission system for protection against lightening. Our procured arrester is embedded with innovative technology and follows all safety standards to give authentic and reliable results. Appreciated for effective protection feature, this arrester is installed over buildings and industries to keep you safe. More to this, rich and flawless functioning of our Liva ESE Lightning Arrester has become a first choice of our valued patrons.
The ESE lightning protectionsystem is in full compliance with French lightning protection standard NFC17-102 & Spanish norm UNE-21186.
The air terminal is EarlyStreamer Emission (E.S.E.) type which is equipped with an upper series ofspark-generating electrodes. The triggering device of the E.S.E. air terminalis sealed in a stainless-steel housing fixed at the center of its central rod.
The air terminal shall be fixedat the top of a GI elevation pole with base so as be at least 3 meters abovethe structure to be protected. Its height above roof level would be dependenton the level of protection and the protection radii required.
The air terminal should beworking on the principle of early streamer emission using non-radio active technology,needing no external power source.
The air terminal should becapable of tracking the lightning stroke minimum 63 micro seconds earlier ascompare to passive lightning rod.
The air terminal is made ofstainless steel and it has qualified diameter to resist high values oflightning currents
Ampress LIVA ESE lightningconductor consists of 3parts: Air Terminal, Ion Generator & Adaptor toconnect with supporting pipe/pole. Ion generator is located in a specialsection which is of stainless body inside and covered with special resin toshield from external effect. As the atmospheric electric field increases duringlightning storm, generator becomes active and ionizes surrounding air.
The air terminal shall havetesting facility to test for its functionality
The vendor shall provideauthorized distributorship letter along with the tender documents
The vendor shall provide METUtest certificate of Ampress lightning terminal in accordance with the testprocedure of NFC 17102 appendix C.
The laboratory photos oflightning terminal during testing shall be provided along with test report withCPRI test report.
The terminal shall haveconformity certificate of valid CE and ISO
The terminal shall have passedthe QAapproval of origin of country
The OEM country origin ofpatent certificate shall be submitted by vendor along with 30yearsOEM warranty with certified hologram.